LED Linear high bay is a durable, heavy-duty construction. High performance, high-efficiency provides a robust solution for high ceiling applications , especially warehouse spaces. Utilizing Samsung LED chips, LED delivers high output performance and quality ilumination. The LHB-S TM customizable optics, installation options, accessories allow each luminaire to be used in a broad variety of applications including warehouses, manufacturing facilities, gymnasiums, commercial facilities, convention centers and more.
Warehouses, Manufacturing facilities, Gymnasiums, Commercial Facilities, Convention Centers.
Fixture body and endcaps are fabricated from aluminum for maximum rigidity.
Lightweight aluminum heat sink designed to perform naturally convective cooling.
Ambient operating temperature 55 °C.
Sansung LED, High efficiency, Optic version 170m/w+, PMMA cover version 130lm/w+L70> 200,000 hours. Utilizes a 90°C case temperature driver for maximum life at high temperatures. 0.90 power factor. Available as 120-277V or 347V input.
General, medium, aisle distributions available to meet both horizontal and vertical light level requirements. Injection molded refractors for repeatable photometry.
5 Year Warranty. See warranty documentation for more information.
Suitable for hanging mount and pendant mount.
1-10V Dimming comes standard. Suitable for use with LED dimmers.
Motion Sensors option available.
Sensor /347V/ Emergency power available.
|JNT05-LHB||55W||120-277V||3000K||S – General (110°)||White||Hanging||No Control Sensor||X1||Y1|
|81W||347V||3500K||M – Medium (90°)||pendant||Emergency||X2||Y2|
|101W||4000K||A- Aisle (45°)||surface||Emergency + Motion Sensor||X3||Y3|
|Input Voltage||120-277Vac, 347Vac||Available CCT||30K, 35K, 40K, 50K|
|Input Frequency||50/60Hz||Projected L70||200,000+ hours|
|Wattage||See Perfomance Table||Power F actor||>0.9|
|Delivered Lumens||See Perfomance Table||THD||<20%|
|Efficiency||See Perfomance Table||Dimming||1-10V|
|CRI||>80||Operating Temp||-20~55 °C/ -4°~131°F|
Read Carefully Before Installing Fixture.Retain These Instructions For Future Reference.
Fixtures must be wired in accordance with the National Electrical Code and all applicable local codes. Proper grounding is required for safety. This product must be installed in accordance with the applicable installation code by a person familiar with the construction and operation of the product and the hazards involved.
WARNING:Make certain power is OFF before installing or maintaining fixture. No user serviceable parts inside.
Mounting Fixture To Ceiling For Vhook Mounting
1.V Hooks (2) and Chain are provided for mounting. Secure V Hooks through Bracket Hole at back of Housing as shown (Fig. 1)
2.Fixture mounting height and spacing should be determined by application requirements.
3.Remove Access Plate and feed supply wire with strain relief conduit connector through Access Plate and make electrical connections as shown in wiring diagram. Use approved wiring connectors and wire to local NEC codes. Push all wires back into Housing. Be careful not to pinch wires.
4.Reinstall Access Plate and secure with suplied Screw(1).
5.If ordered with XXXX sensor or similar sensor or LightCloudn controller, see sensor instruction senclosed.
Focus on providing mong pu solutions for 5 years.